I’m having some weird difficulty wiring this in my WA home. This is to a normal overhead bedroom light. I removed the old toggle switch that had two blacks (assume one load and one line/hot, although not labeled. And connected those to the Jasco. then pulled one of the whites and connected to neutral. Didn’t work.
weird thing (to me) is that I seem to have 3 sets of white, and 6 black wires in the box. I’ve tried quite a few options, some that stopped all power into the room from the circuit (no idea what I did there), some that just don’t seem to power the switch, but are ok with the rest of the room lights (closet, receptacles, etc.).
I thought this one would be easy. Any quick hints on how I might trouble shoot this?