I am replacing the GE 3-way I have installed in my foyer as I cannot get it working no matter how I wired it (candy stripe to hot or neutral both result in dimmed 100% condition many have reported). If I replace it with the HA14WD I have seen many people use, and use a standard 3-way switch as the slave, how does this work? If the light is off and I switch the slave what lighting level do you get, the last one set at the master, or 100%?
It will go to the last Dim Level 8)
No it doesn’t it goes to 100%. Just finished installing it.